Question about Bryant Heating & Cooling
Bryant programmable thermostat has power. Fan will come on manually to test power to thermostat but it will not switch furnace on.
Turn the power off to the Air handler unit.
Remove the thermostat from the wall, (Just the face part).
Look on the back side of the thermostat and verify that the jumpers are set to electric and not gas, otherwise the fan will not run during heat mode, they come from the factory usually set for gas.
If this is a electric heater this will solve your problem, If it is gas then it will be more detailed. Once you put it back on keep in mind that most thermostats have a 3-5 minute delay so just give it a little time and the fan should then work once you have the jumpers in the correct position.
Thank you for using FixYa!
Posted on Nov 17, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 11, 2013 | Honeywell Programmable Thermostat Heater
Nov 02, 2013 | Heating & Cooling
Feb 21, 2013 | Bryant Cube Series 1 Stage Heat/ 1 Stage...
Feb 11, 2013 | Heating & Cooling
Sep 24, 2012 | Lux Tx9100e 7 Day Universal Programmable...
Oct 27, 2009 | Honeywell Programmable Thermostat Heater
Dec 03, 2008 | Hampton Bay 48670 Flemish Pewter Finish...
Nov 24, 2008 | Honeywell Programmable Thermostat Heater
Aug 10, 2008 | Honeywell Programmable Thermostat Heater
493 people viewed this question
Usually answered in minutes!