Question about Empire GWT-25 Wall Mounted Panel Heater
Hi, working with natural gas and converting them over to propane for the country folk, I do indeed know the sound. You might want to take a look at the burner section for any signs of carbon,soot, build up any where.If the gas pressure has changed for some reason, you will get this blow torch sound.You would need the correct meter to check or measure the inches of W.C. Inlet pressure not to exceed 1/2p.s.I. Outlet for propane has changed over the last 10 years, you will now find on the MGV (main gas valve) for propane is almost the same as with natural gas.W.C. is a measurement used in reading gas pressures, stands for inches of water-column. Recommended pressures are well marked in manuals and on valve its self. Right at 2.5 to 4" w.c. So, check for carbon build up and clean if needed.If it burns radical, pressures should be checked with a gas pressure test kit.Yellow Jacket makes a good one. I hope this has been of some help to you, Sincerely,
Posted on Nov 17, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 25, 2012 | Camping, Backpacking & Hiking
Jan 24, 2011 | Goodman Heating & Cooling
Jan 23, 2011 | Coleman Propane Forced Air Heater...
Jan 12, 2010 | Williams 2509612 Ceramic Mid-Size Heater
Oct 29, 2009 | Imperial Commercial Cooking Equipment...
Feb 10, 2009 | GE Profile Spectra JGBP90 Gas Kitchen...
Dec 07, 2008 | Honeywell Power Humidifier: Furnace...
Mar 29, 2017 | Empire GWT-25 Wall Mounted Panel Heater
Dec 28, 2008 | Empire GWT-25 Wall Mounted Panel Heater
431 people viewed this question
Usually answered in minutes!