Question about Goodman GDS80904BNA Open Flame Heater
If your roll out is open it is due to it over heating. Your burners when they are lit are rolling back and opened your roll out. You need to check your exhaust venting to see if is clear(no restrictions). Also, your heat exchanger could be cracked enough that when your indoor fan comes on it puts enough positive pressure on your exhaust that it won't exhaust correctly. One way to check for a cracked heat exchanger is to watch the burner flames when they are lit and see if they move(flutter) or come back toward you when the blower fan starts to operate.I hope I was able to help you!!
Posted on Nov 18, 2009
Hi, I just wanted you to know if you are still having a flame roll out condition, yes the other tech was right by checking for a cracked heat exchanger, or obstruction in the flue. I have seen and found birds nests in the flue on the roof. Also, rusted up burners, plugged burners will cause this. If you have a roll out error, this tells me this furnace is a newer model? The switch will be located at either side near the burners and can be reset after this condition is found. If all appears good, I have seen a gust of wind come through and open the contacts on this roll-out switch. Just food for thought.
Posted on Dec 17, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 17, 2014 | Raypak 406A Digital ASME Natural Gas IID...
Jul 17, 2014 | Goodman Manufacturing Goodman DSXC180601...
Oct 06, 2013 | Rheem 266K to 399K BTU Swimming Pool...
May 18, 2011 | Heating & Cooling
Feb 26, 2011 | Goodman GMS90703BXA Heater
Dec 13, 2010 | Goodman Heating & Cooling
Nov 27, 2010 | Coleman Heating & Cooling
Mar 19, 2010 | Star Enerco Heat HSU45 Garage Heater 45000...
Nov 28, 2009 | Heating & Cooling
1,052 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: