Question about Air Purifiers
Hi, If indeed you do have a heat pump, there wouldn't be any gas involved as a heat pump runs on freon with a reversing valve and heat strips for aux and emerg. heat. For gas electric operation thermostat terminals are rc to rh with factory jumper. Red wire to either.W to W for Heat, Y to Y for cooling G to G for Fan. If you have a blue, you wont need it unless this is a commercial stat useing a common for the Led lights on the stat. The unit will get its 24volts through R terminal in combination with y,w,and,g. Cant be a heat-pump if you have a gas furnace.Wrong t-stat. You need a gas /elect stat. And on a 24volt programmable t-stat, the batterys are used for the program only.If the batterys die, than you will loose the program on most residential stats. On commercial stats with the common in play, when batters die the stat defaults back to the factory settings.If you had a Lennox heat-pump stat on a gas/elect unit, you need to change it. Someone was using what they had on hand. Let me know if this has helped you.I will be here if you need me. Sincerely,
Posted on Nov 17, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 01, 2014 | Honeywell Digital Round Single Stage...
Dec 05, 2013 | Air Purifiers
Oct 15, 2013 | Lennox iComfort Wi-Fi
Oct 13, 2013 | Lennox UV Lamp Replacement Bulb 64X56
Apr 01, 2017 | Honeywell (F50F1032) Air Purifier
Aug 30, 2010 | Honeywell 17000 Air Purifier
Mar 25, 2010 | Honeywell QuietClean HFD-010 Air Purifier
Oct 06, 2009 | Honeywell Enviracaire Elite F300E-1019 Air...
Nov 09, 2007 | Honeywell Enviracaire Elite F300E-1019 Air...
1,034 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: