Question about Honeywell Programmable Thermostat Heater
I have a wall T stat with 2 wires black and white I would like to hooK it up to a 7 day programable t stat. But were do I hook up the wires to. "W" "Y" "G" "R" or "RC" The furnace is a gas furnace.
Show me the steps (short ones) to get this Machine" working right!
Posted on Jan 16, 2008
Don't quite understand the first post.
W is white or heat
Y yellow is cool (or B for blue) either will do
R is red or 24v
RC is the same as R, unless you have separate transformers for heat and cool, place a jumper from the 2 R's
Your old wires, though are 1 white and 1 black, usually this indicates line voltage. 120v or a milli-volt @.750v. Either case, you have the wrong type of thermostat for this application.
Posted on Jan 10, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 19, 2014 | Woods In-Wall Digital 5-10-15-30-Minute...
Jun 18, 2011 | Intermatic Inc. ST01C Digital In-Wall...
Dec 30, 2010 | Garden
Dec 16, 2010 | Intermatic Inc. ST01C Digital In-Wall...
Nov 25, 2010 | Honeywell Focus 6300B 5-2 Days...
Oct 14, 2010 | Honeywell FF12HH Thermostat
Aug 16, 2010 | Intermatic Inc. ST01C Digital In-Wall...
Nov 09, 2009 | Fahrenheat Built-In Baseboard Thermostat...
Mar 07, 2009 | Hunter Fan Company 7-day programmable...
Dec 11, 2008 | Goodman CLQ36AR49 Air Conditioner
Jun 29, 2016 | Honeywell Programmable Thermostat Heater
Apr 27, 2016 | Honeywell Programmable Thermostat Heater
130 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: