Question about Siemens 20Amp 1-pole arc-fault circuit breaker
I have been an electrician for 11 years and when these breakers came out in 2005 what a nightmare. These circuit breakers are extremely sensitive. They are designed to sense loose connections and to protect your house from fires caused by them. By increasing the load (ie. more lights or tv) it increases the size of the "arc" created by the loose connection and the circuit breaker trips before the 20 amp maximum. What I normally find as the cause is a loose connection in one of the receptacles or switches on the circuit. A lot of times, installers will use the "quick stab" inserts on the back of the outlets or switches instead of the side screws. Usually, if you "side screw" all of the receptacles and switches it will resolve the nuisance tripping. One other item that can cause them to trip is too many dimmers on the arc circuit but it doesn't sound like that is the problem you're having.
Posted on Nov 16, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 09, 2016 | Irons
Dec 04, 2015 | Washing Machines
Jan 18, 2013 | Electrical Supplies
Oct 29, 2012 | Challenger Circuit Breaker
Nov 21, 2011 | Electrical Supplies
Jul 08, 2011 | Garden
Mar 03, 2011 | Rowenta Professional DX8800 Iron
Jan 26, 2011 | Televison & Video
Aug 07, 2010 | General Electric 20 Amp, 1 Pole Thick Type...
Dec 17, 2008 | Prime 10 Amp Circuit Breaker
Sep 14, 2016 | Siemens 20Amp 1-pole arc-fault circuit...
791 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: