Question about Honeywell Electronic Programmable Heat/Cool Thermostat - CT3300A100 Heater
Honeywell t8000c display is blank, heat/cooling does not turn on. circuit breaker seems to be fine, main unit is in 'on' position. i toggled the on/off on main unit but still no display. is there a 'fuse' somewhere? or battery? argh... its FREEZING!!! :(
I would say that you have one of two issues. Either your thermostat is bad or you do not have 24v coming from the heating unit. In this case the problem would be in the low voltage circuit of the heater. At the heater you should have 24v AC when you place an electric meter across the R terminal and the C or W terminal. If you have no vaoltage across the R to either the C or W then you have a bad transformer or a blown fuse in the furnace. If you do have voltage ther and also at the t-stat then the t-stat has gone bad, replace it.
Posted on Nov 14, 2009
First, remove face plate and on wall plate you will see about 6 or more straight sensors or prongs sticking straight out towards you, on the bottom. They go into holes on face plate. Make sure they are not bent. If they are bent then, they will not go into the holes in face plate and nothing will appear on your screen nor will furnace run. They are easy to straighten with needle nose pliers, but be gentle so not to break them and when you put face plate back on, do it gently to not bend anymore.
Posted on Oct 13, 2016
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 01, 2017 | Honeywell Heating & Cooling
Dec 09, 2016 | Heating & Cooling
Nov 20, 2014 | Heating & Cooling
Oct 01, 2013 | Honeywell T8000C1010 Digital Programmable...
Sep 28, 2009 | Honeywell Electronic Programmable...
Apr 10, 2009 | LG Art Cool LA121CNP wall/window Air...
Apr 08, 2009 | Honeywell Electronic Programmable...
Jun 12, 2008 | Honeywell Electronic Programmable...
846 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: