Question about Heating & Cooling
Have a york diamond 80 heater/AC unit. When the heater is switched on, the blower comes on at first..but the heater part that usually kicks in after a minute or so, does not come up..AC works fine. Any help is appreciated
Mostly likely the problem is in the pressure switch that tells the board that the blower started and it is okay to fire the burner. The pressure switch is usually a 2" or so round thing about 1" thick, it will have one or two tubes coming out of it that go to the blower or heat exchanger. Make sure that the tube is not cracked or that it has not come off at either end.
The pressure switch can be jumped out to check out if that is the problem, but you need to jump it out after the cycle has started and the switch needs to open after a cycle for the heater to refire again, so that fix would be very temporary. But it may tell you for sure what the problem is.
Posted on Nov 14, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 28, 2015 | Heating & Cooling
Dec 31, 2012 | Heating & Cooling
Oct 06, 2012 | Heating & Cooling
Dec 02, 2010 | Heating & Cooling
Mar 05, 2010 | York Furnace Draft Inducer Blower Fasco #...
Feb 04, 2010 | Heating & Cooling
Oct 12, 2009 | Heating & Cooling
Jun 20, 2009 | York Furnace Draft Inducer Blower Fasco #...
473 people viewed this question
Usually answered in minutes!