Question about Bryant 462AJC021BA Air Conditioner
You have an intermitent short in your low voltage wires. You need to trace the wire all the way to the A/H and then to the condensing unit. I bet you will find a bare spot. Check where the wire goes through the brick to the condensing unit. Ground squirrels are bad about chewing though the insulation. if this is where the short is, replace the wire from the A/H to condensing unit.
Posted on Nov 17, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 06, 2014 | 2007 Citroen Xsara Kombi
Oct 10, 2011 | 2004 Jeep Grand Cherokee
Mar 06, 2011 | GMC Sierra 1500 Cars & Trucks
Jan 09, 2010 | 2001 Ford Focus
Aug 25, 2009 | 2000 Hyundai Elantra
May 31, 2009 | Haier HC48C1VAR Central Air Conditioner
May 28, 2009 | 1999 Dodge Stratus
Mar 27, 2009 | Coleman Mach III Air Conditioner
May 13, 2008 | Panasonic CT-36SL13 32" TV
576 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: