Question about Heating & Cooling
The sensor might be defective and giving a false signal. Also when the unit shuts down they often run a larger shot of condensation out, this maybe tripping the sensor moentarily and giving you the false reading. Check that the line is not partially blocked making the condensate run slow and backing it up for just a second when it dumps after a cycle.
Posted on Nov 13, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 01, 2015 | Goodman Manufacturing Goodman GPH1348M41 4...
Dec 16, 2014 | Goodman Manufacturing Goodman Gas Furnace...
Oct 04, 2014 | Heating & Cooling
Apr 22, 2013 | Heating & Cooling
Mar 19, 2013 | Heating & Cooling
Dec 15, 2010 | Heating & Cooling
Mar 28, 2010 | Dayton Gas Furnace Heater
Jan 31, 2010 | Goodman GMS90703BXA Heater
Oct 07, 2009 | Goodman Heating & Cooling
Oct 25, 2008 | Heating & Cooling
61 people viewed this question
Usually answered in minutes!