Question about Heating & Cooling
There are 3 possible causes for this problem. Either you have low voltage to the motor, you should have 120 volts, or the run capacitor for this motor is defective, or the motor itself is defective (motor windings).If the motor is bad and you replace it make sure you replace the capacitor as well.
Posted on Nov 12, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 24, 2011 | Ducane 30400040 Stainless Steel Grill
Jul 26, 2011 | Ducane 30400040 Stainless Steel Grill
Jun 15, 2011 | Ducane 30400040 Stainless Steel Grill
May 25, 2011 | Ducane 30400040 Stainless Steel Grill
May 10, 2011 | Ducane Affinity 3100
May 14, 2010 | Ducane 30400040 Stainless Steel Grill
Jan 02, 2010 | Reddy HEATER RH170T 165,000-BTU PORTABLE...
Aug 04, 2009 | Ducane 30400042 (LP)
Mar 16, 2009 | Mr. Heater Natural Gas Garage Heater -...
155 people viewed this question
Usually answered in minutes!