Question about Rinnai Toyostove Direct Vent Heater: Laser 30 Toyostove Direct Vent Heater Shipping
I have a Laser 30 in a brand new 24'x24' garage with 9' ceiling, 2"x6" walls(R20) and R40 ceiling. Building is well insulated and very tight. It's been -15 to -20 celsius here lately and it will only make 50 degrees F inside. It is on the high setting and runs steady to do this. Is there something wrong with the heater or is it too small for the application? Randy
I had the Laser 30 serviced a few days ago, and it works properly now. the burner pot was very sooted up, hard crust of carbon in the bottom inch or better which was drasticlly cutting down the heat output(at least 50 per cent) Also put a new fuel pump in and now it puts out a lot more heat. Would strongly advise that these are service at least every two years. Randy
Posted on Jan 26, 2008
Heating and cooling is rated in btu.or could be watts.for your space to be heated quickly to say 70 deg f. you may need a heater with a rating of 36000 btu.it will heat u up then shut off.if you use a smaller heater it will take longer to heat thus using more energy for the same results.
Posted on Jan 08, 2008
Tips for a great answer:
Mar 17, 2012 | Heaters
Feb 05, 2012 | Reddy Heater-30-55,000 BTU Variable
Jun 13, 2011 | Fahrenheat F25426 Electric Baseboard...
Feb 05, 2011 | Fahrenheat Ceiling-Mount Industrial Heater...
Nov 30, 2010 | Fahrenheat Ceiling-Mount Industrial Heater...
Nov 28, 2010 | Reddy Heater-30-55,000 BTU Variable
Dec 23, 2009 | Mr. Heater Natural Gas Garage Heater -...
Nov 17, 2008 | Dayton G73 Utility Heater
Oct 04, 2008 | Rinnai Toyostove Direct Vent Heater: Laser...
91 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: