Question about Heating & Cooling
Check the roll out switch(s) and the lock out switches. They are a small disc looking about the size of a nickle, with with 2 wires attached on them. There will be a re-set button in the middle that resembles a small peg. Push this in to re-set. As the glow coil shorted out, the fuse on the control board may have blown. On the newer furnaces find the main board and look for a car type fuse. If blown, replace. You also have the symptoms of a bad limit switch, by the clicking noise (the heat fan relay) and the blower fan running instantlly.
Posted on Jan 07, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 07, 2015 | Goodman Heating & Cooling
Oct 12, 2014 | Heating & Cooling
Sep 10, 2017 | Heating & Cooling
Nov 13, 2012 | Goodman Heating & Cooling
Oct 07, 2012 | Goodman GMS90703BXA Heater
May 06, 2011 | Bionaire Heating & Cooling
Jan 17, 2011 | Heating & Cooling
Sep 28, 2008 | Goodman GMS90703BXA Heater
386 people viewed this question
Usually answered in minutes!