Question about Heaters
Check the roll out switch(s) and the lock out switches. They are a small disc looking about the size of a nickle, with with 2 wires attached on them. There will be a re-set button in the middle that resembles a small peg. Push this in to re-set. As the glow coil shorted out, the fuse on the control board may have blown. On the newer furnaces find the main board and look for a car type fuse. If blown, replace. You also have the symptoms of a bad limit switch, by the clicking noise (the heat fan relay) and the blower fan running instantlly.
Posted on Jan 07, 2008
Tips for a great answer:
Mar 07, 2015 | Goodman Heaters
Oct 12, 2014 | Heaters
Nov 13, 2012 | Goodman Heaters
Oct 07, 2012 | Goodman GMS90703BXA Heater
May 06, 2011 | Bionaire Heaters
Nov 02, 2010 | Goodman GMS90703BXA Heater
Jan 09, 2010 | Goodman GMS90703BXA Heater
Sep 28, 2008 | Goodman GMS90703BXA Heater
382 people viewed this question
Usually answered in minutes!