Question about Reddy Heater RLP100 Portable Forced Air Propane Heater with Variable Heat Ouput
I recently had a similar problem with my DESA wall-mounted vent-free natural gas heater. We had it repaired but the problem recurred annually until it wouldn't stay on, even on low. There is a part known as an oxygen depletion sensor (sometimes called a flame sensor) that is part of the pilot assembly. When it is working properly, it sends a very tiny current that lets the heater know to keep feeding gas. After a few years the sensor can get rusty, which interferes with its electrical job, causing it to tell the heater to shut off so it doesn't kill you. A temporary repair can be effected by removing the part and cleaning it with sandpaper or emery paper. I suppose compressed air might work too but probably not for long if it is impeded by rust and not just dust. I found all this out from the repairman who thought he had it fixed and then it went out as he was leaving. He couldn't find the part but I found it online at a DESA-authorized distributor and it was about $40. He installed it in about 10 minutes and it has now worked like new (it's at least 15 years old) for over a month.
Posted on Feb 24, 2009
I use canned air and it solves the problem for a while. Shut it off and then spray that where the pilot light is. Wait a little while and turn it back on. Every once in a while you have to clean it out too. I use the canned air at least once every two weeks or mine does what you describe.
Posted on Feb 09, 2008
Make sure that the pilot assy is clean... really clean and rust free. A small wire brush and a toothbrush are two really great tools to use to get that baby clean. If that doesn't do the trick, something else must be wrong and will need to go to the pro's for repair.
Posted on Jan 05, 2008
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jan 01, 2017 | Vanguard Heating & Cooling
Jan 12, 2016 | Heating & Cooling
Feb 16, 2015 | Rheem 43VP50PE2 Power Vent Propane Gas...
Dec 20, 2012 | Rinnai Energy Saver Direct Vent Wall...
Jan 26, 2011 | The Companion Group Kozy World Portable...
Jan 05, 2011 | Vanguard Heating & Cooling
Sep 29, 2009 | Dyna-Glo D-E36 Infra-Red Wall Mounted...
Nov 20, 2008 | Dyna-Glo D-E36 Infra-Red Wall Mounted...
Dec 05, 2006 | Empire GWT-25 Wall Mounted Panel Heater
Aug 02, 2013 | Reddy Heater RLP100 Portable Forced Air...
192 people viewed this question
Usually answered in minutes!