Question about Heating & Cooling
After about 2hours running on cool unit stops cooling inside stays running fan only
I am an electrician
if any one can help to direct me to try solve problem will greatly appreciate it
-Start the unit.
-Press EMERGENCY OPERATION switch.3-minute time delay works.Test run operation operates for 30 minutes.
-Check voltage to terminal block of outdoor unit.Is there 12V DC between 2-1?
-If voltage is presenet check the wiring, compressor contactor outdoor fan motor and compressor.
-If no voltage check voltage to terminal block of indoor unit.Is there 12V DC between 2-1?
-If if voltage is present re-connect the continuity of indoor and outdoor unit connection.
-If no voltage replace the indoor electronic control P.C.
-But also check the coil thermistor sensor and room air thermistor if this two is out of range it can cause the tripping of out door unit. It has the resistance of 8 to 10 k ohms at 25 deg c temp.
Posted on Jan 08, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 25, 2013 | LG LAN186HV / LAU186HV 18,000 BTU 15 SEER...
Sep 18, 2013 | Mitsubishi Heating & Cooling
Jan 21, 2012 | LG LS-L1210CL Mini Split Air Conditioner
Dec 20, 2011 | QMark MUH (0521) Compact Heater
Jul 15, 2017 | LG LS-K1830HL Heat Cool Mini Split Air...
Jan 11, 2010 | Mitsubishi Heating & Cooling
Jan 05, 2010 | Heating & Cooling
Feb 05, 2009 | Mitsubishi MSH09TW Air Conditioner
Apr 20, 2018 | Heating & Cooling
832 people viewed this question
Usually answered in minutes!