Question about Goodman GMS90703BXA Heater
My Goodman heater has had 2 transformers and 4 fuses replaced in a month and the technicians can't figure out why the transformers keep blowing. One time it blew the transformer and not the fuse another time it blew a fuse one day and I had that replaced and then it blew the transformer the next day. All the wires have been tightened each time and we still can't get any long time resolution. Please help. Tonya
If you are where it's warm and you are using air conditioning, have the technician check the coil in the relay in the outdoor unit. I replaced 2 transformers before I figured out the coil was shorted out and drawing too much current.
Posted on Jan 04, 2008
Tips for a great answer:
Oct 06, 2015 | Goodman Heaters
Mar 23, 2011 | Heaters
Feb 09, 2011 | Coleman Heaters
Oct 15, 2010 | Goodman GMS90703BXA Heater
Jun 30, 2010 | Goodman GMS80453ANA Open Flame Mid-Size...
Nov 25, 2008 | Dayton Heaters
Oct 22, 2008 | Goodman GMS90703BXA Heater
Jun 09, 2008 | Goodman GMS90703BXA Heater
Aug 12, 2007 | Goodman GMS90703BXA Heater
394 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: