Question about Sanyo 24KS62R Cool Mini Split Air Conditioner
Ac only systems suct pres climbs to 85 90 then slowly returns to a fluctuating 55 to 65 F server rm at 75 deg, evap blower blows cold but then ambient back to cool, the line length is about 75 ft, more than normal but went to 2 ton to prevent a shortened comp life . Ambient outside is 21 deg F . Could it be the compresser ( scroll ) HP bleeding ove ?
Your suction pressure is erratic, your max. pressure is to much high. You did not measure your unit current reading liquid line press. to complete the data. But the problem of your unit is not the compressor its the system. Try to reprocess the system flush the unit with nitrogen, isolate the capillary tube and flush it with nitrogen to insure that no restriction.
Posted on Jan 04, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 05, 2017 | Heating & Cooling
Feb 24, 2016 | Sanyo Split System Air Conditioner
Aug 05, 2015 | Heating & Cooling
Aug 05, 2015 | AMVENT 18000 Btu 1.5 Ton Ductless Mini...
Jul 23, 2017 | 2001 Dodge Ram 1500 Truck 2WD
Jan 31, 2014 | 2004 Jeep Wrangler
Apr 17, 2013 | Kitchen Appliances - Others
Feb 24, 2012 | Heating & Cooling
Sep 04, 2011 | 1996 Chevrolet Impala SS
274 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: