Question about Soleus KFR-18 Air Conditioner
In the heat mode out door fan cut off
All of the kfr series have a indoor coil sensor that monitors the tube temperature. In the heating mode it will sense for high temp and cut off the outdoor fan to try to lower the indoor coil temp. The cut off temp is 129f, when the coil cools down the fan will cut in and start developing heat again. If the coil continues to get warmer it will shut off completely. The system is either overcharged or the coils and or filters are dirty. All Soleus units need both lines insulated seperately and not together because the metering device is in the outdoor unit. Have your tech calibrate the charge and make sure you clean your filters every 3 months. Removing the sensor will cause the indoor coil to get too hot and possibley start to melt your housing. For further technical questions pleas call 626-378-1518 for technical questions,,professionals only.
Soleus Tech Support
Posted on Mar 13, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Mar 05, 2013 | Soleus KFR-12G Air Conditioner
Jun 17, 2012 | Soleus KFR-18 Air Conditioner
Oct 27, 2010 | Soleus KFR-12G Air Conditioner
Aug 18, 2010 | Soleus KFR-18GW Split System Air...
Feb 20, 2009 | Soleus KFR-18GW Split System Air...
Jan 11, 2008 | Heating & Cooling
Nov 03, 2007 | Soleus KY-34 Portable Air Conditioner
3,695 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: