Question about Heating & Cooling
PSA-RP125GA Fixed Speed Heat Pump
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Dec 31, 2015 | Heating & Cooling
Aug 05, 2015 | AMVENT 18000 Btu 1.5 Ton Ductless Mini...
Nov 30, 2014 | Heating & Cooling
May 26, 2014 | LG LMN127HVT LMN127HVT 12 000 BTU Ductless...
Apr 10, 2011 | Heating & Cooling
Feb 21, 2011 | Sanyo Heating & Cooling
Jul 15, 2010 | Carrier 38CKC060 Air Conditioner
Jan 27, 2009 | Fujitsu 24C1 Air Conditioner
Dec 23, 2008 | Honeywell Electronic Programmable...
Hello Tom , I'm sure i can help you with this.... I work on these units everyday. unfortuneately im not there to put my hands on it but i will explain as clearly as possible. The most common problem I tend to find with these units is that the control board and indoor fan motor tends to go bad in these quite often. If you put the unit in A/C MODE and/or Fan mode and set it to high if it will not speed up from low , then your problem could be in a couple different places. 1st. The bearings in the fan motor could be wearing down , 2nd The Control board could be bad in that its not telling the fan motor to speed up.
And when you tell me that the compressor doesnt run in that mode at any given time..... which the electric heat and heat pump itself works together so that when the load is really tough that the heat pump doesnt over work and in general saves life on your compressor.
Solution is this.
Take your indoor fan motor off and and drill out the rivits and it pulls apart easy, and replace the bearings and grease them.
ALIGNMENT OF THE FAN IS A MUST. doesnt cost much at all the fix this. Just a little time and bearings
Replace the Board in the control box
This my friend will definetly solve your problem. These problems i see everyday with these same units.
Oct 10, 2007 | GE Zoneline Deluxe Series Cooling &...
Sep 20, 2018 | Heating & Cooling
116 people viewed this question
Usually answered in minutes!