Question about Heating & Cooling
Fan run all the time ...will not light burner
This is an easily fixed problem. There are two thermistor switches on Dayton furnaces. One controls the fan motor run function and the heater valve on/off function. The other called a blocked vent switch (located in the top front of the heater) stops the gas valve from opening in the event the
vent is plugged. However, if the furnace was totally shut down for the summer and is now being fired up for winter, the block vent switch has to be reset. The switch has a reset button on it, push it and it should solve your problem. Also, check to make sure the fan run thermistor is clean and does not have debris around it as that acts a insulator for heat to keep the fan run function on.
Posted on Nov 26, 2008
It sounds like you have a couple of problems.
1. fan run all the time. I am sure is your fan delay module.
2. will not light. That would be the gas valve.
call www.grainger.com they can help
Posted on Mar 02, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 21, 2015 | Dayton Heating & Cooling
Nov 24, 2012 | Dayton Gas Furnace Heater
Nov 22, 2011 | Dayton Gas Furnace Heater
Feb 25, 2011 | Dayton Gas Furnace Heater
Nov 13, 2010 | Dayton Gas Furnace Heater
Jan 03, 2010 | Dayton Gas Furnace Heater
Dec 08, 2009 | Dayton Gas Furnace Heater
Dec 03, 2008 | Dayton Heating & Cooling
Nov 20, 2008 | Dayton (3E379) Heater
514 people viewed this question
Usually answered in minutes!