Question about Eva-Dry EDV300 Dehumidifier
Have kenmore 5020... works fin in summer time, but w/ furnace on, the coils frost up after a short time of running... the house is at 68-70 when I turn it on... not sure how to take off the front cover and clean the coils.. and other ideas?
I believe a dehumidifier is supposed to operate in temps above 60 degrees. Even though your house is warmer than that, the air entering the dehimidifier may be getting into that range due to it being on a basement level etc. This is perfectly normal and is not a malfunction with your humidifier.
Your options are to either place the dehumidifier closer to a heat source in order to keep the air which is entering warmer. (I've even heard of someone placing a light bulb in front the unit during winter to warm the air slightly as it enters). Because the dehumidifier's coils get cold in order for it to collect moisture from the air, if they are freezing, giving the unit a rest for a few hours every few hours may allow the coils to thaw in between and prevent them from reaching freezing temperatures while running. You could use a timer to accomplish this, but you'll want to insure that it's a commercial grade timer in order to handle the electrical draw that the dehumidifier requires.
Posted on Jan 05, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 27, 2013 | Kenmore Dehumidifiers
Aug 19, 2011 | Edison 40 Pint Dehumidifier
Mar 11, 2011 | Kenmore 54701 Dehumidifier
Sep 04, 2010 | Comfort-Aire Dehumidifiers
May 17, 2010 | Goldstar DH304 Dehumidifier
May 01, 2010 | Kenmore 53509 Dehumidifier
Jul 18, 2009 | Kenmore 54501 Dehumidifier
Jul 02, 2008 | GE AHG40LJ Dehumidifier
Feb 16, 2008 | Kenmore 53301 Dehumidifier
516 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: