Question about Williams 2509612 Ceramic Mid-Size Heater
Wall heater willams 3509622 heats up then shut down pilot too. i change the thermocouple all ready
There are 2 things to check. First is the thermostat. Next is the thermal safety switch located up on the heat exchanger. by-pass these one at a time by connecting the wires together. If that solves the problem, change to a new one. If neither one of these items are bad, you need a new gas valve.
Posted on Dec 31, 2007
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 30, 2011 | Rheem 40 Gallon FVR NATGAS Low WATER...
Apr 21, 2011 | Heating & Cooling
Oct 30, 2017 | Williams (5009622) Ceramic Gas Wall...
Nov 12, 2009 | Dyna-Glo RMC-8001SS Heater
Nov 10, 2009 | Heating & Cooling
Nov 07, 2009 | Dyna-Glo D-E36 Infra-Red Wall Mounted...
Oct 10, 2009 | Desa International Blower Glow Warm Wall...
Nov 20, 2008 | Dayton Heating & Cooling
Nov 17, 2008 | Desa International Blower Glow Warm Wall...
354 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: