Question about Water Heaters
My Paloma tankless water heater turns on for a minute or two and then shuts off and flashes a C2 11 error code - what do I do?
I just had the same problem and I fixed it in about an hour or 2.
First shut off the gas,water and power(unplug it)
Take off the cover
There are about 20 screws above the electrical circuit board.
You have to remove all of those screws to remove plate that is covering the burner assembly.
The burner assembly has these 3 pins that look like number 7's
these are covered with build up and gas can't flow right.
That's why you get the c211 error not enough gas.
Take a wire brush and gently remove any build up,
I also cleaned the thermocoupler which is next to the burners.
It looks like a metal pin with a couple of wires coming out of it this was also very dirty.
I took a can of air and basically freshened it up
It works perfect now.
Email me with any Q's at Mario@myredr.com
All that you need is a long phillips screw drive and a drill because its about 25 screws
The burner assembly has 2 screws all the in back underneath the assembly once you remove those 2 the assembly comes out . You don't have to disconnect any wires.
Posted on Oct 29, 2009
After following Mario's instructions I was unable to find the '3 pins that look like 7s', but I'm certain this is due to the multiple different models and configurations of Paloma's. However, I was able to get it to function properly... so far. While the code may indicate that the unit isn't receiving enough "fuel", I wonder if this could also mean oxygen, as air is required to allow for combustion. If the vent on the front of the unit is clogged with dust, it would be the equivalent of a carburetor running too rich. Unfortunately, I came to this realization after spending a couple hours disassembling and reassembling the unit. I had just done some sheetrock and mudding on the wall right next to where the unit is housed, and the dust from that as well as what has accumulated over the last couple years had left a layer that was certainly blocking some air-flow. So before you try your luck as to whether your unit disassembles in the same way Mario's does, check this first. It's the screen right on the front of the panel. Just a thumb screw is holding it on.
Posted on Jan 06, 2010
HAHA, check the simple stuff first. i found this forum when my water heater started flashing this error code. after taking some of the steps offered here it dawned on me that i had turned off the gas valve to the water heater thinking that i was turning off the valve to the furnace in the garage for the summer. DUH. always check the simple stuff first
Posted on Jun 29, 2013
There is even a better way but it does involve much more disassembly. There are two flame rods at the back of the burner assembly that you cannot get to unless you remove the burner assembly, which is what I did. Otherwise, you can only clean the three in the front of the burner assembly. There is an engineering manual available on the Paloma website that details major component removal and lots of diagnostics, including all voltage and resistance specs for the major components. I used fine sand paper on each igniter and flame rod, then brushed the burner assembly with a stiff paint brush. I happened to have a code 12 but it was acting just like was stated.
It now works better than it has in a long time. Those things get a crud buildup. The discoloration from being in the flame does not go away but the crud sure does.
Posted on Apr 12, 2013
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
did you check the filters on the the water valves, i am not exactly sure about your codes that are shoeing but if you could read it and post them, i know on some of the units 76 means there is low water pressure and the filters are behind 2 caps one on each side above the shut off valve take off the caps and remove the screens, clean them and replace them ,, make sure you turn off the water on both side first or you will get wet
Posted on May 29, 2009
Tips for a great answer:
Feb 14, 2014 | Rheem Paloma Tankless Water Heaters...
Aug 19, 2013 | Rheem Paloma PTG-74PVN / RTG-74PVN...
Mar 20, 2013 | Rheem Paloma PTG-42PVN / RTG2-42PVN...
Aug 09, 2012 | Water Heaters
Mar 30, 2011 | Rheem Paloma PTG-74XP / RTG-74XP Liquid...
Dec 29, 2010 | Rheem Paloma Tankless Water Heaters...
Feb 28, 2010 | Rheem Paloma PTG-74PVN / RTG-74PVN...
Nov 16, 2009 | Rheem Paloma Tankless Water Heaters...
Nov 03, 2009 | Rheem Paloma PTG-74PVN / RTG-74PVN...
May 18, 2009 | Rheem Paloma PTG-74PVN / RTG-74PVN...
7,588 people viewed this question
Usually answered in minutes!