Question about Air Conditioners
You said that the elements are fine. How do you know that. How are you checking. Just having continuity won't do it. Remove the wires from the element and check from one side to ground to make sure it's not grounded. By switch do you mean breaker? My money is on a bad element.
Posted on Jan 17, 2009
You should have 24vac at the 2 lowest terminals 1 on each side of the sequencer with a call for heat.( that is the control voltage,the terminals are usually double spade brass in color) If you have the control voltage after about 30-120 seconds the sequencer should close.The voltage reading across the sequencer should go from 230vac to 0 volts when the sequencer closes.If you have control voltage and 230vac on each side of the sequencer then the sequencer is bad.It is beast if replacing the sequencer replace by moving 1 wire at a time from the old to the new.And ALWAYS make sure power is truned off.
Posted on Dec 29, 2007
Tips for a great answer:
Aug 26, 2011 | Air Conditioners
on Dec 04, 2009 | Air Conditioners
May 26, 2011 | Dometic Rooftop RV Air Conditioner
Feb 26, 2011 | Air Conditioners
Jan 12, 2011 | Premier 52PQ2153 Air Conditioner
Nov 23, 2010 | Maytag Electronic Portable Air Conditioner...
Jun 14, 2009 | Intertherm P3RA-048K Air Conditioner
Apr 02, 2009 | Air Conditioners
Jan 17, 2009 | Air Conditioners
May 17, 2008 | Air Conditioners
172 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: