Question about Heating & Cooling
You said that the elements are fine. How do you know that. How are you checking. Just having continuity won't do it. Remove the wires from the element and check from one side to ground to make sure it's not grounded. By switch do you mean breaker? My money is on a bad element.
Posted on Jan 17, 2009
You should have 24vac at the 2 lowest terminals 1 on each side of the sequencer with a call for heat.( that is the control voltage,the terminals are usually double spade brass in color) If you have the control voltage after about 30-120 seconds the sequencer should close.The voltage reading across the sequencer should go from 230vac to 0 volts when the sequencer closes.If you have control voltage and 230vac on each side of the sequencer then the sequencer is bad.It is beast if replacing the sequencer replace by moving 1 wire at a time from the old to the new.And ALWAYS make sure power is truned off.
Posted on Dec 29, 2007
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 04, 2018 | Water Water Heaters
Jan 03, 2015 | Maytag MEW6530DDS Stainless Steel Electric...
Dec 19, 2010 | Water Heaters
Aug 02, 2009 | Dryers
Mar 28, 2009 | GE DBSR453EBWW Electric Dryer
Mar 08, 2009 | Hotpoint Dryers
Feb 18, 2009 | Belling Ovens
Jan 17, 2009 | Heating & Cooling
Dec 16, 2008 | GE JRP24 Electric Double Oven
May 17, 2008 | Heating & Cooling
178 people viewed this question
Usually answered in minutes!