An expert who has written 20 answers of more than 400 characters.
Re: HEATER IS JUNKY
Sounds like you have a blockage to the main jet. If you have a
compressor just blow the jet out from the top and with a bit of luck it
will clear it. If not you may need to remove the outer covering and
find the pipe to the main jet and again using compressed air just blow
it out. Usually not much goes wrong with these apart from blockages
every now and then and most of the servicing places just blow them out
with compressed air. Just make sure if you remove a pipe you tighten
the pipe up properly when re-fitting it. Hope this helps.
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones). click here to download the app (for users in the US for now) and get all the help you need. Good luck!
- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
Turn the gas knob to the pilot setting, press it in and hold it. You should hear gas escaping while in this position. Do not let more than about 10 seconds of gas out at one time as it may pool. Light the pilot while holding the gas knob down for a minute. Release the gas knob (the pilot flame should stay lit) and turn it to the ON position. To make sure the gas heater is working properly, turn up the thermostat and see if the heater heats up. How To Light The Pilot Light On Gas Heater
First locate where to light pilot. You can do this by following thin aluminum colored tubing from control valve to inside heater.In general on top of your gas control valve is a knob. Turn indicator of this knob to pilot and depress knob. This will start gas flow to pilot at end of thin tube. Hold this knob in the depressed position and light pilot. DO NOT release knob for 30 -45 seconds. Then release knob and pilot will remain lit. Then turn knob to on position. If pilot will not stay lit you may need a new thermo coupler, which senses heat from flame to keep pilot gas flow open.
Turn the Gas Control Knob inside the heater compartment from OFF to PILOT. Push in the knob and hold it, at the sametime push the ignitor button (will probably be a Red button). Once the pilot lights, continue to hold the Control Knob down for one minute. Then ease off of it. If the pilot stays lit, turn the Control Knob to the ON position. The burner should light, if the Thermostat is set higher than the ambient temperature in the house. If the Ignitor button doesn't work, you can match light the pilot. Just be careful and follow the instructions above, once it's lit.
You will first need to turn the control knob to pilot. Then depress the control knob button and hold it. Then press the push button piezo igniter several times until pilot lights or open pilot inspection cover and manually light pilot with match/lighter. You may need to hold the control knob for at least a minute. Then release the control knob and if the pilot stays lit then turn the control knob to on. If it does not light then repeat the process again.
There should be instructions on the inside of the heater access door. Make sure you are comfortable working with gas heaters. Make sure the shutoff valve supplying gas to the heater is on. Turn the gas valve to "pilot", press and hold it while attempting to light the pilot. Once the pilot is lit, continue holding the gas valve knob down for about 30 seconds. The pilot should stay lit once you release the knob. If the pilot stay lit, turn the gas valve to "on". Replace the heater access door and make sure you have proper water flow and attempt to light the heater. If it will not light, or the pilot will not stay on, you will probably have to replace the pilot generator. It provides voltage to run the heater and after time it wears out and produces less and less voltage. A millivolt heater runs on less than one volt so any power loss can be a problem. If you are able, test the pilot generator with a multimeter to see if you are getting at least 500mv when the pilot is on. If not, you should replace the pilot generator or even the entire pilot assembly. Hope this helps...
Do you have the serial number or the manufacture date? There are some design changes and I would need to know the year of manufacture to assist accurately. Usually it is a relay or the thermocouple connection that will affect the unit staying lit.