Question about Heating & Cooling
My art cool split keeps displaying a "ch" followed by an "s" and the unit is stopping--any idea what this is
CH5 is a communication error between the indoor and outdoor unit. The thermistors have nothing to do with this error code. Check the communication wire for continuity, make sure it is shielded and stranded wire.
Posted on Jun 05, 2009
Try to unplug the unit or “off” after 10sec. “on” the circuit
breaker and then start the unit.
But if the defect persist then you need a qualified technician. The below error may be the cause of unit failure.
- Out of range thermistor is also can also be the cause of tripping outdoor unit with matching blinking light same as low refrigerant.
- Dirty indoor and outdoor can also be the cause
Remote control units have diagnostic program in the
control, after 3 to 5 minutes of operating if the diagnostic
tools detect abnormal operation, then its shutdown the unit
to protect from damage. Thermistor sensor is one of the
parts that detect the operation of the unit. Out of range
or defective thermistor can shut the operation of the unit.
- If your indoor and outdoor is clean start the unit in cool mode and monitor the outdoor pipes. If your suction pipe is icing or dry then your unit is under charge, but if your suction is cold and sweating then the system is ok and sure that the thermistor sensor is defective.
- Out of range thermistor sensor in both return air and freeze up sensor can cause the tripping “off “ the unit. The resistance of both thermistor is 8 to 10k ohms, so can test by using ohm meter
Posted on Jan 26, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 11, 2011 | LG LSC183VMA Split System Air Conditioner
Dec 13, 2010 | LG Art Cool LA121HNP Split System Air...
Jul 09, 2010 | LG Art Cool LA121CNP wall/window Air...
Apr 30, 2009 | LG Art Cool LA181CNW Split System Air...
Apr 18, 2009 | LG Art Cool LA121CNP wall/window Air...
Mar 21, 2018 | Heating & Cooling
927 people viewed this question
Usually answered in minutes!