Question about Dayton G73 Utility Heater
Unit runs ok with top cowling off, but with cowling on unit dies out with in sceconds. Unit has a new air pump installed and a new ignitor. Hopefuly you can help us.
I have the same type problome with the model 3VE50A 125,000 BTU if the upper cowlen is off it runs fine but as soon as you put the cover on it shuts down all of the filters have been cleaned per the manual and i have installed all new fuel lines ,air lines and have adjusted the pump pressure to the sujested 5 PSI
In the original manual for 3E219B it does say the pressure shoule be 5psi. If you would like I can email you a copy of the mail just email me at firstname.lastname@example.org. As for the 3VE50A you can go to http://www.bealsmotor.com/heathogprices.html and click on the model and find the correct pressure for that heater. There is also a place to order parts. Check to be sure you have no air leaks in the filter cover or air lines or fittings, clean filters and then adjust your pressure.
Posted on Jan 21, 2012
Who told you air pump is supposed to be 5 psi? at the desatech site in their PDF troubleshooting guide air supposed to be 3.0-3.5 psi.
Posted on Dec 27, 2007
Tips for a great answer:
Jan 14, 2011 | Dayton E52 Utility Heater
Feb 10, 2010 | Dayton (3E386) Heater
Feb 06, 2010 | Dayton Gas Furnace Heater
Jan 14, 2010 | Heaters
Dec 12, 2009 | Dayton Heaters
Jan 31, 2009 | Reddy Heater-170,000 BTU Kerosene Deluxe
Jul 08, 2008 | Dayton E51 Oil Filled Utility Heater
Dec 21, 2007 | Dayton E52 Utility Heater
Jan 31, 2013 | Dayton G73 Utility Heater
261 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: