Question about Goodman GMS90703BXA Heater
I have been having intermittent problems. Before the blower fan would wait too long to kick in and hit the high limit and would shut things down and then the blower would run till it cooled off and then it cycled again. Now the vent fan (exhausts gases) is running intermittent..it pulses on and off and of course shuts the burner down so all I get is cold air. But sometimes it runs sometimes it doesn't. The technician replaced the control board for the second time( to correct the timing of the blower) ..didn't change anything so the tech installed a relay to bypass the blower control so now the blower starts when the thermostat calls for heat and now I am having pulsing with the vent fan..this unit is driving me to drink! any suggestions appreciated?
Does this piece, have an economizer and or vent draft options installed? I hope not. If not, I had the same sort of problem with a Payne unit, sort of the same style. First things first. bypass the thermostat by making a jumper or connecting the red to the white wire on the thermostat, see if that stops the problem. Repair techs are all to anxious to replace the board anymore. If the repair man installed a relay to bypass the blower control he is in over his head, the limit switch determines when the fan shuts on & off based on temperature. There is a relay on the control board that basically carries the load for the motor. Dont have anything else installed that need not be there (there is enopugh crap already from the factory) If you want to really fix this I need to know if you have and can read a volt/ohm meter and can understand a wiring diagram, hopefully yours is still there. let me know after the thermostat thing and I can walk you through this.
Posted on Dec 25, 2007
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Oct 31, 2017 | Heating & Cooling
Feb 03, 2015 | Heating & Cooling
Nov 01, 2013 | Goodman GMS90703BXA Heater
Aug 14, 2017 | Goodman GMS90703BXA Heater
Nov 17, 2011 | Goodman Heating & Cooling
Sep 06, 2011 | Goodman Heating & Cooling
Jan 14, 2011 | Goodman GMS90703BXA Heater
May 09, 2010 | Omega Trane Furnace Draft Inducer Blower...
Jan 02, 2010 | Goodman GMS90703BXA Heater
340 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: