Question about Goodman CLQ36AR49 Air Conditioner
Check and see if the fan will turn easily by hand. Do not put your hand inside with the power on. Turn on unit, take a small stick and try to turn the motor. if the motor starts and runs then you capacitor is probably bad. if the motor is hard to turn then the motor is bad.
Posted on Oct 08, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
The first thing I would check is the breaker/disconnect that feeds your outside unit with electricity. If it seems fine then i would check the electrical contact/relay that energizes the compressor. Low voltage from your thermostat is sent to a small coil in the contact/relay that is energized to pick up a set of contacts. These contacts allow the supply voltage to flow through them to turn on your compressor and fan. If your thermostat is in the on position, have an electrician use a meter to see if there is voltage on either/both sides of the contact. If it is only on the supply side, then you probably have a bad contact. Fairly inexpensive fix if you are a do-it-yourselfer. Also, make sure that your thermostat is sending out a signal to the contact. A meter will show you a low voltage signal if it is working.
Posted on Oct 09, 2009
Tips for a great answer:
May 06, 2017 | Heating & Cooling
Jan 17, 2018 | Ruud Heating & Cooling
Jul 17, 2010 | Heating & Cooling
May 23, 2010 | Goodman CKL24AR24 Air Conditioner
Oct 07, 2009 | Goodman Heating & Cooling
Jun 22, 2009 | Heating & Cooling
May 31, 2009 | Ruud UBHC Air Conditioner
May 07, 2009 | Heating & Cooling
96 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: