Question about Goodman Heating & Cooling
The first thing I would check is the breaker/disconnect that feeds your outside unit with electricity. If it seems fine then i would check the electrical contact/relay that energizes the compressor. Low voltage from your thermostat is sent to a small coil in the contact/relay that is energized to pick up a set of contacts. These contacts allow the supply voltage to flow through them to turn on your compressor and fan. If your thermostat is in the on position, have an electrician use a meter to see if there is voltage on either/both sides of the contact. If it is only on the supply side, then you probably have a bad contact. Fairly inexpensive fix if you are a do-it-yourselfer. Also, make sure that your thermostat is sending out a signal to the contact. A meter will show you a low voltage signal if it is working.
Posted on Oct 09, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 06, 2017 | Heating & Cooling
Jun 02, 2014 | Ruud Central System Air Conditioner
Jul 17, 2010 | Heating & Cooling
Jun 09, 2017 | Heating & Cooling
May 23, 2010 | Goodman CKL24AR24 Air Conditioner
Oct 07, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 19, 2009 | Ecoquest Flair Air Purifier
May 31, 2009 | Ruud UBHC Air Conditioner
Oct 27, 2007 | Ruud UBHC Air Conditioner
70 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: