Question about Heating & Cooling
Gmh95/gch9 manual calls for 3 inch exhaust pipe? 3 inch seems large for a 90k btu..I was going to run 2 inch book says 3...the run is about 18 feet..Thanks!
Furnaces must be vented EXACTLY as specified by the mfr or you WILL have problems - they spend a lot of time and money coming up with those specs. then design the furnace based on them.
Posted on Oct 07, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
May 26, 2014 | Motorsports
May 01, 2011 | Goodman Heating & Cooling
Mar 30, 2011 | Water Heaters
Mar 24, 2011 | Exhaust for Nissan 200SX
Mar 27, 2010 | Goodman Heating & Cooling
Jan 30, 2010 | Goodman GMS90703BXA Heater
Oct 11, 2009 | Pentair MASTER TEMP HEATER 400 000 BTU NG...
Oct 10, 2009 | Heating & Cooling
Apr 18, 2009 | Heating & Cooling
151 people viewed this question
Usually answered in minutes!