Question about Heaters
I have a Goodman heater that will not do a full cycle without shutting down? it runs for a few mins and then shuts down and gives code 1. If i shut it down by shutting all power off to the heater, it will refire for a few mins and shut down again.
Not having a model number to help you with, I can only give you generic info. Typically a flashing 1 represents that the furnace has exceeded its allowed attempts to start. Not much help. If I can suggest removing the access panel on the furnace and tape down the door safety switch. That being done, have a helper turn up the thermostat and you get your head inside the furnace cabinet and document what it does. It should first blink on the LED indicating a call for heat. Next the inducer blower should start up (the small blower hooked to the exhaust pipe). Next you may see an orange glow where the burner is. There should be a small clear port where you can watch this. Next some clicking should be heard from the gas valve. Then the orange glow should turn to a blue flame. This flame should travel all the way right and left igniting all the burners. Then it should stay on until the call for heat is satisfied.
After doing this and with your model number, get back to us and we may be able to pin-point your issue.
Posted on Dec 24, 2007
Tips for a great answer:
Jan 29, 2016 | Goodman Heaters
Dec 16, 2013 | Goodman Heaters
Oct 22, 2013 | Goodman GMS90703BXA Heater
Jan 16, 2012 | Goodman Heaters
Nov 17, 2011 | Goodman Heaters
Nov 05, 2010 | Goodman GMS90703BXA Heater
Jan 23, 2010 | Goodman GMS90703BXA Heater
Dec 20, 2009 | Goodman GDS80904BNA Open Flame Heater
Oct 19, 2009 | Goodman GMS90703BXA Heater
Apr 23, 2009 | Goodman GMS90703BXA Heater
Oct 20, 2016 | Heaters
280 people viewed this question
Usually answered in minutes!