Question about Goodman Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
There is a vacuum sensor on most units tied from the exhaust gas fan to the sensor. Does the unit try to start? If the unit's exhaust fails to pull the switch it will turn off after about 30-45 sec after starting. "IT" thinks it's not exhausting and stops to keep from overheating. Do you have this exhaust fan and rubber hose to sensor? Can you see if that fan is turning on start?
Posted on Nov 10, 2007
Ok, you either have a inducer fan issue or a pressure switch issue or a plugged vent pipe. The inducer turns on to establish a draft for the exhaust. If it is not working you will get this error code. If the pressure switch does not sense pressure caused by the inducer, it will give this code. If either the intake pipe or exhaust pipe is blocked (even y just a little) it will give you the same error code. If the condensate hose or receptical is plugged, again it will give you this error code. Good Luck!
Posted on Oct 21, 2008
After fighting this thing for 2 weeks, I changed out the circuit board tonight and I have heat!!!! Barnett Brass is where I got it. $100
Posted on Nov 14, 2008
I Also have the same and other problems with my furnace model # GDS80703AXBB. First the LED kept blinking 4 times and I too jumped the primary limit, that didn't kelp. After several attemps I moved the wires going to the circut board and everything starting working again. After a week It stopped working again, so I pulled the plug out of the circut board checked all wires for for a bad connection plugged it back in. Now the LED blinks 6 times again I move the wires. Then the LED blinks 3 times. Then the transformer burns out. I have burned out 2 transformers and I have ordered a new circut board.
Posted on Nov 15, 2008
This is probably a dry bearing in the vent motor. Those motors run at high RPM's and can make a deafening high pitched squeal if they become dry and need oiling.
Some of the motors have oil cups on them for dripping oil into and others;s are much more difficult as you need to guess where the bearing is and try to drip oil down into them or run the oil to them.
Any light weight small motor oil ike a sewr machine oil will work.
Many hardwares have small oil bottles with extending spouts made just for oiling motors for just a couple of bucks...
The other thing that can cause this is if the blower wheel is coming loose and has moved to the side and is hitting the side of the blower housing. Take the bottom cover off and check for play or movement side to side in the blower wheel. Spinning it with the power off by hand may give you a clue as you will hear it scraping the side of the housing.
Posted on Dec 29, 2009
Tips for a great answer:
Dec 17, 2014 | Goodman Manufacturing...
Dec 01, 2012 | Heating & Cooling
Nov 23, 2011 | Goodman Heating & Cooling
Nov 18, 2011 | Goodman Heating & Cooling
Jan 31, 2011 | Goodman Heating & Cooling
Nov 16, 2009 | Coleman Propane Forced Air Heater...
Oct 19, 2009 | Goodman Heating & Cooling
Feb 16, 2009 | Goodman GMS90703BXA Heater
126 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: