Question about Rinnai Desa Vent-Free Infrared Gas Heater: Vent-Free Infrared Gas Heater(18,000 BTU)
I have a glowarm heater that I used for one season last year. I've been using it for a bout a week now and this morning when I got up it had shut itself off. I started it back up and when I went into the room it was off again. What do I need to do? There is plenty of air flow. This is an old house and not air tight at all. Thanks for your help.
I have had the same problem and I think I fixed it. Near the pilot light you have the part that shots the spark (electric ingitor?) behind it is another brass part which I beleive is flame sensor, what I did to fix it is losen the philips screw that holds the two in place then pushed the flame sensor higher so the pilot light hits it more, then just tighten it back up. I hope it helps....
Posted on Dec 12, 2008
Near to where the fire plate is there is a high temperature limit that is connected by two wires to the pilot millivolt generator. try relocating this limit further away from the flame jet. it too might be faulty - go to desatech dot com for a new limit.
Posted on Dec 25, 2007
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Oct 27, 2015 | Heating & Cooling
Dec 06, 2009 | Desa International Blower Glow Warm Wall...
Oct 18, 2009 | Desa International GWP20T GLOWARM Wall...
Jan 27, 2009 | Desa International GWP20T GLOWARM Wall...
Jan 16, 2009 | Desa International GWP20T GLOWARM Wall...
Nov 03, 2008 | Desa International Blower Glow Warm Wall...
Feb 07, 2008 | Heating & Cooling
1,200 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: