Question about Ruud Matching Split Air Conditioner
I have a gmp075-3 when you go to turn the heat on the burners ingnite like there supposed to all three light up then after 10 15 sec they shut down it will do this over again and then the blower will come on anyway and it will blow without the burners on also during the summer i notice even with the thermostate switch off the blower would come on by it self off and on usally i would call a tech out but my wife was laid off so money is tight but i am diseal tech and im pretty electrical and mechanicaly incline if someone can point me in the right direction i will greatly apppreciate it. Its starting to get cold down here i memphis. also i heard there supposed to be a fault light on it and where would the location of the circuit board be thank you for your time
Ok check yoour air flow sounds like its tripping out on high temp
the blower comes on too cool the eqipment
you may need to clean the coils on top of the bloower
Posted on Oct 05, 2009
I would try cleaning the flame sensor. I also have a ruud furnace and it has done the same thing. Take a piece of sandpaper and . clean the sensor. It does not recoginize the flame and shuts the gas off. This is why it will start and then shut off.
Posted on Oct 06, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 20, 2015 | Heating & Cooling
Oct 06, 2014 | Coleman Propane Forced Air Heater...
Dec 20, 2011 | Honeywell L4064B2236 Fan/Limit Control...
Oct 30, 2010 | Heating & Cooling
May 13, 2010 | Ruud UBHC Air Conditioner
Mar 22, 2010 | Ruud UBHC Air Conditioner
Dec 21, 2009 | Heating & Cooling
Dec 04, 2009 | Refrigerators
Jan 15, 2009 | Central Dual Temperature Heat Gun Kit...
348 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: