Question about All-Pro Heating & Cooling
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: charmglow gas patio heater
The ticking noise is the ignigtor. If the gas tank is full, and the regulator is on, then try lighting with a match or fire of some sort. Be careful of the spark-er! If it lights, then the spark needs to be adjusted so it catches the gas better. If it doesn't lite, then the hole for the pilot is plugged. An outside heater is common for a spider or other creature to make this his home. You need to clean it out. Compressed air even another flame may do it. if not It needs to be removed and cleaned out. If you can see the little hole, trey poking a thin piece of wire into it, it may get it.
Posted on Mar 20, 2008
I have several of these heaters in my rent houses and love them. The most problem I have is not being able to ignite the pilot with the user control igniter. Remove the screws that hold the front cover in place along with the front cover. Hold the pilot control down and ignite with a lighter. Keep the pilot engaged until thermocouple is warm enough to keep pilot gas flowing. If it will light this way then you need to blow out the pilot orifice. It seems that every year I have to go in after the summer season when the heater is off and clean the pilot/orifice lines with high pressure air. I believe spiders/bugs/dust block pilot orifice when it is not in use. You can also tell that orifice is blocked when you don't get a good blue pilot flame with pressure behind it allowing the flame to submerse the thermocouple. If the the thermocouple is not getting enought heat it will turn pilot gas off for safety reasons.
Posted on Dec 06, 2009
Is there a frost line on your LP tank, if so you may need to replace the tank with a larger tank or refill your tank. This can happen if the tank your using is too low or too small (use 100 lb tank or greater). If there is no frost line it may be an issue with the thermocouple. The manufacturer offers a service manual and owner's manuals on there site. This should assist you... www.desatech.com Thank you
Posted on Jan 28, 2010
Problem: Your furnace will not ignite the gas to
produce heat for your home. When a furnace has a bad ignitor what I see most of
the time is the following sequence of operation:
1. Thermostat calls for heat. 2. Draft inducer motor starts. 3. Pressure switch attached by a small plastic or rubber tube senses the negative pressure produced by the draft inducer and closes. 4. Draft inducer runs for 30 seconds to a minute before you hear a gas hissing sound. The ignitor did not glow, the flame sensor (a small metal probe about 1/8" in diameter, with a white porcelain base) does not sense the flame, so after 8 to 10 seconds the hissing sounds stops with no ignition of gas to heat your home. Your furnace shuts down and goes into a lock out condition until you turn your power switch back off and on again. Then the sequence starts all over again with no ignition of the gas. Solution:You probably need to purchase and install a new ignitor. I would suggest that you inspect your ignitor closely for cracks. Make sure you do not touch the ignitor with your bare hands. If you do not visually see a crack, then you could have a furnace control board problem or a limit, rollout switch problem. The furnace's control board might not be supplying the voltage to the ignitor. If your furnace lights and the gas stays on for 8 to 10 seconds, then shuts right back off, then you need to clean your flame sensor with light sand paper or steel wool. You might need a new flame sensor, but most of the time they can be cleaned an will work well after cleaning.
Posted on Nov 30, 2010
Testimonial: "I'll replace the igniter to see if it's the cause, thank you very much."
Tips for a great answer:
Dec 23, 2014 | All-Pro Heating & Cooling
Dec 09, 2014 | All-Pro Propane Garage Shop Heaters - All...
Aug 09, 2014 | Hayward H Series Pool & Spa Heater 200k...
Aug 11, 2013 | General Electric Water Heaters
Dec 10, 2011 | Teledyne Laars Laars Lite 2 Pool Heater...
Dec 01, 2010 | All-Pro Propane Garage Shop Heaters - All...
Apr 26, 2010 | RTO Atwood Water Heater - 6 Gal LP
Mar 13, 2009 | Reddy Heater-30-55,000 BTU Variable
May 06, 2017 | All-Pro Kerosene Garage Shop Heaters - All...
29 people viewed this question
Usually answered in minutes!