Question about Honeywell Power Humidifier: Furnace Humidifier/ Humidifier
HOW DO I CONNECT TO THE 24 VAC --- FOR THE HUMIDIFIER TO COME ON ONLY WHEN THE BLOWER IS ON?
I FOUND THE 24V (A BLUE AND YELLOW WIRE) FROM THE TRANSFORMER, BUT CONNECTING TO THEM MAKES THE HUMIDIFIER REMAIN ON ALWAYS.
NEED TO FIND A WAY TO GET THE 24V ONLY WHEN THE HEAT IS ON.
UNIT IS A LENNOX (MODEL) G41UF-48C-110-02
If you have 1220v eac terminals you may use those but a current sensing relay is the right way
Posted on Oct 28, 2009
You can hook it to R and W on the board but you should really use a current sensing realy on the blower so it wont come on until the fan is running and you should also have a humidistat
Posted on Oct 04, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 26, 2015 | Honeywell HE120 Humidifier
Jan 22, 2012 | Honeywell HE220A1019 Whole House...
Feb 21, 2011 | Humidifiers
Dec 29, 2010 | Aprilaire 700 Humidifier
Apr 03, 2010 | Honeywell HE360A1027 Whole House...
Feb 15, 2010 | Aprilaire 700 Humidifier
Nov 18, 2009 | Honeywell HE360A1027 Whole House...
Feb 06, 2009 | Aprilaire 700 Humidifier
Nov 24, 2008 | General Filters 1042-LH Humidifier
Dec 15, 2014 | Honeywell Power Humidifier: Furnace...
477 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: