Question about Sloan Regal Flushometer 111 Toilet 1.6 Gpf
SLOAN FLUSH VALVES ARE SIMPLE. IT DEPENDES ON THE PROBLEM. IF THE VALVE KEPS RUNNING AFTER IT IS FLUSHED THE RUBBER DIAPHRAM IS DIRTY OR OLD AND THE RUBBER DIAPHRAM IS GETTING HARD. AND STICKING. THE VALVE WORKS ON A VACUME TO CLOSE THE DIAPHRAM TO STOP THE FLUSH PROCESS. WHEN YOU PULL ON THE FLUSH HANDLE YOU BREAK THE VACUME THAT FORM ON THE TOP OF THE DIAPHRAM WHICH ALLOWS THE WATER TO FLOW AS THE WATER FLOWS IT IS ALSO STARTING TO PULL A VACUME IN THE TOP OF THE DIAPHRAM TO CLOSE THE DIAPHRAM AND STOP THE FLUSH.
AS THE DIAPHRAM GET OLD AND WORN IT GETS HARD AND DOES NOT MOVE AS FREELY AND STICKS OPEN AND WON'T LET THE VACUME CLOSE THE DIAPHRAM AND THE URINAL WILL CONTINUE TO FLUSH. HOPE THIS ANSWERED YOU QUESTION
Posted on Oct 01, 2009
GO TO SLOAN .COM
Posted on Dec 05, 2012
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 26, 2015 | Sloan 180-1 Exposed Urinal Flushometer -...
Jan 17, 2011 | Sloan 180-1 Exposed Urinal Flushometer -...
Mar 29, 2017 | Sloan Regal Flushometer 111 Toilet 1.6 Gpf
Aug 20, 2010 | Sloan 3010100 110 Water Saver 3.5
Jun 15, 2010 | Sloan Regal Flushometer 111 Toilet 1.6 Gpf
Nov 21, 2009 | NRS 180-1.5 Sloan Exposed Urinal...
Nov 20, 2009 | Sloan 180-1 Exposed Urinal Flushometer -...
Sep 19, 2009 | Toto TEU2DNS-11 Commercial Electronic...
Jun 21, 2009 | Home
Dec 19, 2008 | Kohler Flush Actuator K 9446 [ Bathroom,...
1,003 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: