Question about Goodman GMS90703BXA Heater
This is a pressure switch error.
You could have a couple of issues which could cause this code.
There could be a blockage in either the intake or the exhaust pipes.
The easiest way to check for this is to undo the coupler on the intake pipe inside the furnace housing and let it draw in air from the furnace room for a couple of minutes and see if that is a fix.
I have done the same with the exhaust, but only for a minute to check for a blockage(as you will create some CO while operating this way).
The drain sometimes causes problems. I have had to use a small piece of wire(like a coat hanger) and push through the fitting at the bottom for the collector box before, where the hose ties onto the furnace burner box.
If you have a build up of condensation in the secondary heat exchanger this can cause problems.
The easiest fix for this is to ensure the furnace is sitting with a slight tilt to the front(like 1/8th inch back to front), so that the condensate runs to the collector box and out into the drain.
You could also check to make sure that the vent motor is getting up to speed (just in case a bearing is getting tight and slowing it down enough to not let enough flow through to trip the pressure switch.
Use a brad nail and poke out the intake from the blower to the p-switch... and that is probably the issue here.
Thanks for using FixYa!!
Posted on Oct 01, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 21, 2012 | Heating & Cooling
Nov 08, 2012 | Goodman GMS90703BXA Heater
Oct 12, 2011 | Goodman GMS90703BXA Heater
Dec 24, 2010 | Goodman GMS90703BXA Heater
Dec 02, 2010 | Goodman GMS90703BXA Heater
Feb 18, 2010 | Goodman Furnace Draft Inducer Blower ...
Dec 11, 2009 | Goodman GDS80904BNA Open Flame Heater
Dec 02, 2009 | Goodman GMS90703BXA Heater
Oct 12, 2009 | Goodman Heating & Cooling
20 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: