Question about Ruud UAMB Air Conditioner
I have a heat pump that freezes up every once in a wile. and does not give off good heat. the temp outside is about 37. can youhelp me.
Simple solution that works every time...turn your A/C on for 5-10 minutes...CASE SOLVED
Posted on Nov 26, 2008
YOU HAVE ONE OF SEVERAL PROBLEMS , FIRST AND EASIEST TO REPAIR KEEP FILTERS CLEAN REPLACE EVERY 30 DAYS , #2 LOW CHARGE WILL CAUSE ICE ,# 3 A FAULTY INTERMITTENT FAN CONTROL SWITCH ,THIS WOULD BE MY # 1 GUESS SINCE I HAVE SEEN IT MANY TIME OVER THE YEARS , #3 WOULD BE A FAULTY DEFROST CONTROL BOARD OR SENSOR , THE REASON I LEAN TOWARD THE FAN CONTROL IS YOU SAY THE ICE IS ALSO IN THE INSIDE UNIT AND THIS IS MOST COMMON WITH RESTRICTED AIR FLOW OVER COILS AND SOME TIMES THE FAN SWITCH WILL CAUSE THIS PROBLEM THE DISCHARGE TEMPERATURE IS DIRECTLY RELATED TO THE TYPE OF UNIT ,TYPE OF REFRIGERANT IN SYSTEM AIR BALANCE CFM OF FLOW MANY VARIABLES IN THIS EQUATION,CANT SAY
Posted on Nov 24, 2008
Icing up on the outside unit of a heatpump is normal in cold weather. your heatpump should go into a defrost cycle on a regular basis when its that cold.
as far as not good heat goes, when it gets colder outside there is less heat in the air for the heatpump to pickup and put off inside your house. on a 40 degree day the air temp will probably be only around 100 dgrees coming out of a vent. compared to a gas or oil furnace that puts out about 130-150 degree air it feels very cool.
hope that helps..
Posted on Dec 21, 2007
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 27, 2012 | Goodman Heating & Cooling
Dec 27, 2012 | Jandy Aqualink Rs4 One Touch Control...
Dec 26, 2009 | Heating & Cooling
Dec 20, 2009 | Heating & Cooling
Dec 17, 2009 | Aprilaire 600 Humidifier
Sep 18, 2009 | Heating & Cooling
Jul 30, 2009 | Ruud UBHC Air Conditioner
Sep 27, 2008 | Heating & Cooling
Jun 03, 2008 | Danby 3.6 cu. ft. / 102 liter Chest...
Aug 08, 2013 | Ruud UAMB Air Conditioner
726 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: