Question about Goodman PHKJ048-1 Air Conditioner
I just installed a reversing valve in backwards. It was an honest mistake. All brands except ruud and rheem energize the valve in the cool mode. If u make the same mistake I did its an easy fix. First u can't just change the the orange wire from o to b. keep the orange wire on o. U need to install a 24 volt relay in the heat pump. Wire the coil with a common and remove the hot wire from the reversing valve and land it on the coil of the relay. Next wire 24volt hot to oneside of contacts on relay and run a wire from normally closed terminal on relay to reversing valve. What this does is reverse the contacts. So ur heat pump will work normal and also be able to go threw a defrost cycle as well. Hope this helps.
Posted on Aug 02, 2012
You should be able to move the reversing valve wire from O terminal, (the changeover relay), on the thermostat to B terminal. I deal mostly with York
which O on the t'stat is normally open and B is normally closed.
Posted on Oct 06, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 01, 2009 | Goodman Heating & Cooling
Apr 27, 2009 | Goodman CLQ36AR49 Air Conditioner
Mar 29, 2009 | Goodman GMS90703BXA Heater
Nov 11, 2008 | Goodman Heating & Cooling
Oct 19, 2008 | Goodman Heating & Cooling
Nov 25, 2007 | Goodman CLQ36AR49 Air Conditioner
Dec 11, 2011 | Goodman PHKJ048-1 Air Conditioner
807 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: