Question about Heating & Cooling
Thermostats call for the heater relay to engage, try jumpering the W and R terminal at the furnace with all other wires disconnnected from cuirciut board, if heat comes on your t-stat is bad.
Posted on Oct 01, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 01, 2017 | Carrier Heating & Cooling
Nov 15, 2012 | Soleus Air KFHHP-22 22000 BTU Mini Split...
Nov 14, 2012 | Briggs & Stratton Starter Scott's Equip...
Dec 02, 2011 | Jandy Lite 2 Natural Gas Pilot Light...
Aug 03, 2011 | Carrier Heating & Cooling
Jan 14, 2011 | Valor Toys
Jun 25, 2009 | Kenmore 76081 Wall/Window Air Conditioner
Jan 11, 2009 | Carrier 38CKC036 Air Conditioner
136 people viewed this question
Usually answered in minutes!