Question about Heating & Cooling
Carrier gas furnaces will try to light three times then will usually go on a lockout for one hour you can bypass the lock out by resetting the power, turn furnace on, remove wires from gas valve, you will need a multi meter to check for voltage to valve, if control board sends a call to the gas valve the valve is bad, if voltage is never present during the lighting cycle your control board is bad
Posted on Sep 30, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 29, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Mar 13, 2010 | Carrier Heating & Cooling
Jan 19, 2010 | Carrier 38CKC036 Air Conditioner
Jan 10, 2010 | Heating & Cooling
Jan 10, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 24, 2009 | Carrier Heating & Cooling
Nov 28, 2009 | Carrier 38CKC042 Air Conditioner
Nov 06, 2009 | Heating & Cooling
Oct 22, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Oct 17, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
274 people viewed this question
Usually answered in minutes!