Question about Goodman CLQ36AR49 Air Conditioner
Most likely couse is the indoor fan stops working
the elements get to hot they should be a safty for each element some snap to open the circuit
or they have things that look like gray resters
that may be open but you can not tell witch an ohm meter to check if they are good
Posted on Oct 30, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Sep 11, 2013 | Ruud Heating & Cooling
Jun 26, 2011 | Goodman Heating & Cooling
Jun 10, 2010 | Heating & Cooling
Apr 07, 2010 | Intertherm P3RA-024K Air Conditioner
Sep 22, 2009 | Bryant 463AAC008BA Air Conditioner
Jul 28, 2009 | Heating & Cooling
Jul 12, 2009 | Heating & Cooling
May 19, 2009 | Sub-Zero 642
May 09, 2009 | Carrier Heating & Cooling
Oct 12, 2008 | Whirlpool 10 cu. ft. / 283 liter Chest...
26 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: