Question about Coleman Propane Forced Air Heater w/Electronic Ignition (50,000-80,000 BTU)
Have a Coleman Evcon Propane unit and the blower runs continuously (and combustion blower). I have done the following.
-Disconnected thermostat wiring.
-Check function of both limit switches.
-Centrifugal switch on combustion blower working.
-Gas valve working.
-Not sure about glow igniter. Reads resistance. Circuit board sending about 2V. Doesn't heat up.
-Circuit board LED indicates no problem (continuous).
Any ideas or other checks?
Only way to make blower stop is to turn off power.
You should be seeing 120 volts to the igniter. Anything less requires either a replacement of the transformer, start relay or control module.
Posted on May 30, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 17, 2013 | Coleman 7990-319p Evcon Gas Furnace...
May 07, 2017 | Coleman Propane Forced Air Heater...
Nov 24, 2010 | Coleman Propane Forced Air Heater...
Jan 18, 2010 | Coleman Heating & Cooling
Jan 13, 2009 | Coleman Propane Forced Air Heater...
Dec 16, 2008 | Coleman Propane Forced Air Heater...
May 30, 2008 | Heating & Cooling
May 15, 2014 | Coleman Propane Forced Air Heater...
1,243 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: