Question about GE Quiet-Aire Ductless Split System Air Conditioner AS1CD12AA0/AS0CD12AA0
The ductless mini splits, can be a bit tricky,,, most of them,, you feed the outdoor unit with a 220 volt line, then 4 wires run from the outdoor unit to the indoor unit.
The outdoor unit is the one that supplies power to the indoor unit, usually, 4 wires, run from the outdoor unit to the indoor unit.
So you have 2 leads and a ground that feed the outdoor unit,,
G - ground,, and a L1 and a L2,, these are the terminals that you feed your 220 volt to the outdoor unit,, then 4 wires from the outdoor to the indoor unit,, usually 120 volt is fed over these wires to run the indoor unit blower and a digital signal is also run over these wires as well as the 120 volt current,, just make sure that the marked terminals are matched on the outdoor and indoor unit;
Example: If there is a S1 terminal outdoors, make sure that the same wire hooks up to the S1 terminal on the indoor..
Hopefully no damage has been done to the indoor unit.
This being said,, allot of brands use a variaty of wiring connections, what I discribed above is a more normal setup.
That wiring schamatic will be your guide.
I hope this helps,,
Have a great Day,
Posted on Mar 30, 2010
Check your comm board you need to make sure both are set to the same settings
Posted on Oct 05, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 11, 2014 | Dometic Rooftop RV Air Conditioner
Jun 14, 2010 | Heating & Cooling
Mar 01, 2010 | LG LS-L1210CL Mini Split Air Conditioner
Apr 24, 2009 | Heating & Cooling
Apr 02, 2009 | Heating & Cooling
Jan 17, 2009 | Heating & Cooling
Jan 12, 2009 | Heating & Cooling
Jul 23, 2008 | Carrier Heating & Cooling
May 17, 2008 | Heating & Cooling
632 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: