Question about Goodman GMS90703BXA Heater
3 flashes indicate an issue with either the inducer, pressure switch, plugged condensate drain or a venting restriction.
Clear all debris from the exhaust and intake air piping. Make sure they are not drooping anywhere.
Check the pressure switch and the rubber hoses for blockage.
Blow out the drain line that evacuates the condensation.
On the inducer motor housing, un- plug the rubber hose going to the pressure switch and check to see if there is suction when the motor is running.
Make sure your air filter is clean.
Listen to the inducer motor as it turns for gurgling or any other abnormal sounds.
To make the heater run while you have the cabinet open, tape down the door safety switch. Remove the tape after diagnosos.
Posted on Dec 19, 2007
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jul 19, 2013 | Sharp Cv-p12lx 11500 Btu Portable Air...
Apr 23, 2011 | Heating & Cooling
May 17, 2010 | Goodman CKL24AR24 Air Conditioner
Nov 07, 2017 | Samsung HLT6187SAX 61" DLP HDTV
Jan 30, 2010 | Heating & Cooling
Dec 23, 2009 | Amana PTH123B25AJ Heat Pump Air...
Dec 08, 2009 | York Furnace Draft Inducer Blower Fasco #...
Sep 22, 2009 | 1998 Ford Mustang
Apr 18, 2009 | Fujitsu 24R1 Air Conditioner
168 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: