Question about Heating & Cooling
I have a Rheem gas furnace, model RGPN-10EAMER. The blower unit appears to work but air is not (noticeably) blowing from the ceiling air ducts. The burner unit is working fine. How do you adjust the blower speed to increase the air flow?
Look at circuit board and follow wires that come from fan motor, if this is a standard motor black is high and it will be going to a prong that says cool, red is low and it will go to heat, you will have a yellow and a blue that are "parked" remove red park it were the blue is and put blue on heat, if this is a variable speed motor you will have to set dip switches via your equipment manual
Posted on Sep 30, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 05, 2018 | Heating & Cooling
Nov 26, 2014 | Rheem Gas Furnace 75000 Btu 80% Afue. Rgpn...
Oct 19, 2012 | Rheem Gas Furnace 60000 Btu 95% Afue. Rgrc...
Jan 15, 2012 | Rheem Heating & Cooling
Sep 26, 2010 | Heating & Cooling
Dec 17, 2009 | Dayton Gas Furnace Heater
Jul 24, 2008 | Heating & Cooling
863 people viewed this question
Usually answered in minutes!