Question about Intertherm P3RA-048K Air Conditioner
I have an intertherm MGHA-090AAAPQ-01. I cannot get the pilot to light. I took of the pilot line at the control box and there is no gas coming out there. I tried it with every possible valve combination. I have no owners manual for the furnace
There should be a reset button in the upper chamer next to the fan motor. In the middle ,push in on the center red button to reset it, this tripps because it says I,m not gettig enough air flow due to a plugged or dirty fliter located on the front cover or door.
Posted on Dec 18, 2009
If there are two wires to gas valve check voltage between these two wires while the furnace is going through a start up if you never get a call or voltage to valve your control board is bad, if you are getting voltage ,your valve is bad
Posted on Sep 29, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Mar 07, 2018 | Intertherm Heating & Cooling
Jan 06, 2015 | Intertherm Heating & Cooling
Feb 05, 2013 | Intertherm Heating & Cooling
Oct 24, 2012 | Heating & Cooling
Aug 26, 2010 | Heating & Cooling
May 02, 2010 | Heating & Cooling
Jan 02, 2010 | Heating & Cooling
Jan 09, 2009 | Intertherm P3RA-048K Air Conditioner
Aug 16, 2008 | Heating & Cooling
2,325 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: