Question about Heating & Cooling
Turn off the power to the air handler(indoor unit). Remove the access panel. From the motor,trace the wires back to the fan relay. One wire will probably trace back to the incoming power terminal. The other is the fan relay. It could be intermittent thermostat signal to the relay or a bad relay.
To verify if the fan motor is good,you can remove the one wire from the relay and re-attach it to the other side of the incoming power terminal. If it runs OK there,replace the relay. If it does not run,replace the blower motor.
Posted on Sep 28, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 01, 2014 | Carrier Heating & Cooling
Apr 09, 2014 | Frigidaire Heating & Cooling
Jun 30, 2012 | Heating & Cooling
Jul 21, 2011 | Ruud UBHC Air Conditioner
Aug 13, 2010 | Ruud UBHC Air Conditioner
Aug 08, 2010 | Ruud Matching Split Air Conditioner
Jan 08, 2010 | Mitsubishi Mr. Slim MXZ30TN Air...
Jul 20, 2009 | Goodman CKL42AR42 Air Conditioner
Apr 28, 2009 | Heating & Cooling
Aug 26, 2007 | Ruud UAKA037 Air Conditioner
251 people viewed this question
Usually answered in minutes!